By offering 30 minutes integrity and 30 minutes insulation, APOLLO LITE™ 30:30 exceeds the minimum requirements relating to Cavity Barriers as detailed in the UK Building Regulations: Approved Document B (Fire Safety). FIREFLY™ is manufactured using specially treated woven glass fibre fabrics. FIREFLY™ APOLLO LITE™ is lightweight and easy to install.
|DESCRIPTION||Lightweight, non rigid Fire Barrier - Combined Insulation and Integrity|
|CERTIFICATION||Third Party Certified by IFCC. Certificate number: IFCC 1461|
Description: Non-toxic / user friendly / flexible / durable
Easy to manipulate and cut to shape
Colour: White / Black
Coating: A chemical treatment to optimise thermal properties and help prevent fire migration
Minimum Thickness: 6mm
Vertical: Exceeds 30 minutes integrity with 30 minutes insulation when tested to BS 476 parts 20/22: 1987 Exova test reference number 402913*
*Tested at Exova Warringtonfire. Satisfies the requirements of UK Building Regulations: Approved Document B (Fire Safety) for fire IMO Resolution MSC.61(67) Part 1. Non Combustibility
|ASSESSMENT IFCC||Fields of Application covering extended drops, penetrations, ceiling systems, widths and installation requirements|
|CLASSIFICATIONS||LPCB Non Combustible
WIRA BS476 part 7 Surface spread of Flame Certification to Class 1 Pass
WIRA Tested to BS476 parts 6 and 7 pass
|SOUND REDUCTION INDEX||14dB As a stand alone product
44dB When installed in conjunction with a mineral fibre type ceiling
|DIMENSIONS AND PACKAGING||Width: 127cm
Roll Length: 6 linear metres
Roll Area: 7.62 square metres
Packed: Concertinaed and individually wrapped in polythene
Minimum Weight: 1.44 kg / m2
|FIREFLY™||All FIREFLY™ products must be installed in compliance with the FIREFLY™ Installation Guide, which is provided upon request. Deviation from these drawings should not be carried out without written authority from the FIREFLY™ Technical Department.
All figures quoted are nominal, believed to be true at the time of printing and are presented without guarantee. It is up to the user to determine the suitability of use.